- Products & Solutions
- All Industries
- About Us
A. The UP2000 is designed to operate under an infinitely variable set of operating pressures, flow rates, and wide range of temperatures. In very rare applications, a certain unique combination of flow and temperature may cause the regeneration membrane valve to vibrate at an audible frequency that produces a hum-like tone (pressure regulators will sometimes do this as well for the exact same reasons). There are three possible remedies for this:
A. The UP2000 dryers are factory set to produce a -40 PDP for the rated flows under fully saturated conditions at 100psig/95°F. However, the dryer is still useable within the ranges of 60psi-225psi and 40-125°F when we change the regeneration airflow throttle orifice size.
A. If the dryer is not needed, it can be put into “stand-by mode” by making a connection between terminals 1 and ground on the Hirschmann-type connector (see Figure 1). This connection is usually made by a relay, but can also be accomplished by other means such as a manual switch or a process integrated relay. In this mode, the dryer will continue to allow air flow but will not consume any power or use air for regeneration.
A. As depicted in Figure 2, a relay control (max. 45VDC / 200mA) can be operated directly between terminals 3-ground in the event the dryer indicates an alarm or service condition. During operation the relay is normally closed and open during an alarm and/or service event. If a diode is not already integrated with the relay, make sure to connect one in parallel to protect the electronics of the dryer. Refer to Figure 2 for dryer-side connection to the Hirschmann connector.
The dryer shall be installed on a sturdy, level surface. The weight of the dryer should be transferred to the supporting structure by the feet rather than the connecting pipework. When fastening the inlet and outlet piping, a suitable wrench should be used to counteract the tightening force as to not allow this torque to be transmitted to the dryer. A good method is to use an adjustable wrench to hold the aluminum block that contains the threaded female connections while tightening the connections. Please reference Figure 3.
It is recommended that the dryer be installed with a three-valve bypass arrangement so that compressed air can be distributed even while the dryer is being serviced. An example of this arrangement is shown below:
3. Clearing the Desiccant Service Light (standard version only)
After desiccant cartridge replacement, the controller must be reset. Before performing the procedure, be sure the unit does not have power.
As shown in Figure 4, the reset switch is located in the control block. Remove the two screws along with the cover to expose the reset switch. Flip the reset switch to the other position and re-install the cover.